Use this page to find all the information you need on responsibly disposing of commercial climate control waste.
What is climate control waste?
Climate control waste is liquid waste from any heating, cooling, ventilation, air conditioning or
refrigeration system consisting of:
- waste from cooling towers that are dedicated to and are an integral part of any of these systems, and/or
- waste from condensate, de-frost water or chiller water.
Can climate control waste be discharged to sewer?
Customers may apply for a permit to discharge climate control waste to sewer. Residual sludge
from membrane scraping and descaling must not be discharged to sewer. It must be disposed of
off-site in accordance with the requirements of the relevant regulatory authority such as local
Cooling tower waste
Cooling tower water is usually dosed continuously with anti-corrosion chemicals and biocides while
the system is operating. Some installations however have a drip feed which means that the
chemical is being dosed 24 hours a day, whether the plant is operating or otherwise. Water is fed
in automatically (make-up water) to compensate for losses and bleed-off (draining).
Effects of water conditioning
The chemical dosing reduces the risk of corrosion and diseases such as legionaires' disease but
increases the incidence of scaling, while the bleed-off reduces the scaling but enhances corrosion,
disease risk and slime formation within the pipework.
The composition of the chemical formulations varies considerably. Four general groups of anticorrosion
chemical formulations can be identified. These groups are based on chromate, zinc,
tannin and phosphate compounds. Among the biocides, some formulations are organochlorine
Maintaining system water quality
For maintenance purposes and to remove accumulated sludge, cooling tower waste is usually
dumped at about 3 monthly intervals but sometimes as frequently as monthly. There's also a
small continuous bleed-off to prevent the concentration of scaling materials.
Generally, all other waste from climate control systems including condensate, de-frost water and
chiller water does not come in contact with chemicals, nor is it dosed with any chemical
formulations. This must not be discharged to the sewerage system.
Under exceptional circumstances, providing the quantity is very minimal, approval may be given
for the waste to discharge to the wastewater system. The applicant must clearly demonstrate that it's not economically viable to discharge this waste to the stormwater drainage system.
The main exception to this rule is liquid waste generated by scrubbers associated with fume hoods
and trade or laboratory air extraction systems, which may have become polluted by contact with
chemical vapours. Sometimes scrubbers associated with fume hoods in trade laboratories must
have waste neutralised by pH dosing.
This waste is to be managed the same as cooling tower waste.
Premises wishing to discharge climate control waste to the wastewater system must apply for an trade waste
Trade waste application
The application must be accompanied by:
- Material Safety Data Sheets (MSDS) for all the chemicals to be used, and
- Laboratory analysis of the waste to be discharged.
Customer charges are based on the metering of bleed water, which is mentioned in our typical drawings for trade waste.
Cooling towers typical drawing HX33-018- 040
Commercially confidential proprietary formulations will be processed in the strictest of confidence.
Pre-treatment to reduce chrome and zinc may be required and is determined in accordance with our acceptance criteria.
Acceptance criteria for trade waste